Power (watts): 16w
Light output (lumens): 1600 lm
Expected Life (hours): 15000 Hrs
Colour temperature (CCT): 4000 Cool White or 6500k Daylight
Colour rendering index (Ra): 80
Beam angle (degrees): 210°
Power Factor: > 0.5
Lamp cap: T8 (G13)
Dimms: 1212.5mm pin to pin, 25.5mm width, 193 grams
T-8 conventional luminaire perfectly.
> The SubstiTUBE® Tube must be handled with care, and do not operate the product that in a damaged condition.
> When operating with CCG (magnetic ballast), SubstiTUBE® Starter has to be inserted to replace
the conventional fluorescent lamp starter. If the conventional starter is not replaced, the
SubstiTUBE® Tube will start blinking and be damaged!
> Do not use SubstiTUBE® Tube in luminaires which do not have any conventional starter
or whereby the conventional starter cannot be replaced. Otherwise, rewiring is needed.
> Not suitable for luminaires with serial lamp connection i.e. more than one tube at one magnetic
> The SubstiTUBE® Tube emits light at limited angle, unlike conventional fluorescent tube
in 360°Omni direction.
> Due to the light distribution characteristic of the SubstiTUBE® Tube the resulting luminaires light
characteristic is likely to change. It is not guaranteed that e.g. standards for lighting at working
places will be complied with after replacement. A photometric check of the installation is highly
> The effective energy savings depend on the efficiency of the luminaire setup to be replaced and
should be considered individually in each case. Particularly magnetic ballast losses are reduced
to ohmic losses and are normally only about 1W.
> The SubstiTUBE® Tube is protected according to IP20. Applications with external risk of
moisture and dust can be served with an adequately protected luminaire.
> SubstiTUBE® products differ in their diameters and geometries from fluorescent lamps. Their
use in open batten luminaires with gaskets is possible if no excessive force is expended during
the fixing. Obtaining the necessary IP protection in open batten luminaires with gaskets cannot
> SubstiTUBE® Tube may also be driven directly on line voltage. In order to grant a safe operation
mode please refer to the installation instructions for further information.
> Photobiological Safety of lamps and lamp systems according to IEC 62471. Risk Group: Exempt